GST has substantial experience with all types of end-to-end testing using both the Doble F6150 (at both ends) and the AVO MPRT (at both ends). Both test sets use a GPS clock to trigger at a specific time and can be used to simulate practically any event at both ends of the line. The benefits of end-to-end testing include the following:
Discover incorrect settings that result in unexpected (nuisance) or inappropriate trips
Determine transmission time delays that could result in coordination problems
Verify the correct operation of all kinds of communications-assisted schemes
Completely test the overall performance of a protection scheme with real secondary fault currents at each end
GST also has the ability to analyze the data created during these tests. We have the experience and equipment required to extract the oscillography from the relays and compare it against the expected results. We can then verify correct timing down to a fraction of a cycle. These services allow the customer to have a history of how the relay should react during certain faults (Zone 1, Zone 2, Reverse, etc.). With this knowledge, the customer can react quickly and confidently to determine the cause of a fault and reenergize the line.
GST Power Service Group, Inc. HEADQUARTERS; 2801 Remington, Suite #3, Fort Collins CO 80525 Phone: (970) 204 1279 or Toll Free (866) 675 1279 Fax: (970) 204 6648